Tank Comments on State street
On 12/19/2003 checkup number DOEINS168123 was carried out. The Historic Dept Of Environment was alarmed because of tank comments. The object of this control was a building located at 8259 State street. The report from this investigation was last verified on 01/01/2011. An examinator responsible for this case commented: facility id:2007012 upgrade permit 107673 new sumps were installed at each submersible pump short runs of piping were installed that were necessary to be removed in order to install the new sump containment the primary piping was tested on 12/19/03 at 5psi and passed the existing secondary containment piping is open ended at both ends and thus cannot be pressure tested the facility does have intersitial monitoring, the contractor has installed new dispenser pans and at each dispenser pan a liquid sensor these, along with sensors in the new sumps will act as secondary method of detecting a leak from the piping .